RWS-150/15/28 Controller and Lock Power Modules.
New Controller and Lock Power Supplies. Same Specifications /
New Mounting Bracket.
RWS-150/15/28 Installation Instructions
New DSX-LAN-D and DSX-IP-HUB
These units are programmed with a web browser. They have a
default IP address of 192.168.1.25. The DSX-LAN-D is the
latest in LAN communications interface and can replace all older
DSX-LAN modules. The DSX-IP-HUB is a communication distribution
module allowing the Master to Communicate with the Slave
Controllers via IP without the use of PC Master Software. The Links below
are to the installation and configfuration documents.
DSX-LAN Module 2016
The Link below will allow you to download the following files
for programming the new DSX-LAN Module:IPSetup.exe,
DSX and the Proper Cable
Below is a link to the DSX Cable Specifications. These
are the cable specifications for all generations of DSX
These specified or equivalent cables are the only ones
DSX will support. These are the cables tested with the
system and approved by UL.
CAT 5 cable should only be used for network connections
to the DSX-LAN (M) module. IT SHOULD NEVER be used for panel
communications, reader connections, lock wiring, internal
controller wiring or anything else. It will not function
properly for panel communications. You will have problems if
you use the wrong cable!
No Communication to the Master Controller can be due to
several errors in configuration among other things such as
firewalls. In WinDSX it is important to check these items:
There must be a Device 0 defined under Devices. In
Location/Numeric Options Tab/ Connect Type must be Drect for
all LAN,USB,Serial Communications.
There must be a unique Comm Port defined. For LAN
communications the Port Type must be LAN TCP/IP, The IP
Address must match that of the LAN module. The Transmit Port
(TXIP Port) must match the Recieve Port of the LAN Module.
The Receive Port (RX IP Port) is typically 0 but if defined
must match the Transmit Port of the LAN module. Look at
configuration examples in LAN module instructions for more
information on how to make these settings correctly.
“Error 9” when trying to edit System Parameters or Location is caused by the
increased number of regional time zones in Windows. Accommodations for
Microsoft’s time zone structuring have been provided in our latest software releases.
The problem should not appear with WinDSX 3.7.139 and higher.
“Operation Must Use an Updateable Query” is typically caused by inadequate
Windows permissions to the files in the target Path to Database. Usually seen when
adding Workstation PC’s to an existing system.
Software Version 3.7/4.7 and higher has a new feature that allows
Time Zone Linking. This new linking logic will only work if all of the controllers in
the location are of 1040 Series, 1022, or 1032 controllers with the 1030PR5 retrofit
processor. All controllers in the location will require V3129 or higher. This feature
cannot be used if any of the controllers are of the old style 1030 Series or 1021. The
3.7/4.7 versions also require new updated versions of PC Master and Soft I/O.
If WinDSX ever generates a C++ error when starting, check the WinDSX/Errors
sub folder. If it exists, double click on cserrorlog.txt to open in Notepad. Scroll
down to the last entry in the file. If you see a reference to ‘Unrecognized database
format, C:\WinDSX\alarm.mdb’, close Notepad, delete any files in the Errors folder,
then delete alarm.mdb in the WinDSX folder. Run Repair and repair the existing
database. Then modify the update.txt to have a 1 instead of a 0. Save it close it and
re-Start WinDSX and verify that the program runs OK.
“TCP/IP Lost” or “Comm Loss” in the Red Box in the lower right corner of
Workstation indicates that the IP settings of the Comm Server PC are not set
correctly or not operating properly. Areas to check include:
Start>Settings>Control Panel>Network>Protocols>TCP/IP>Properties. A
WinDSX Communications Server PC
have “Use the following IP”
selected if this PC is on a Network, with a number that matches what is in the
Single Right Click Network Neighborhood>Properties>Services, the presence of
Simple TCP/IP or SNMP can disable WinDSX's ability to run CS.EXE, remove
these or use another PC as the Communications Server.
Single Right Click Network Neighborhood>Properties>Services, MS Internet
Information Server can disable WinDSX’s ability to run CS.EXE. Remove this
or use another PC as the Communications Server.
Single Right Click Network Neighborhood>Properties>Services, Pier to Pier
Web Services can disable WinDSX’s ability to run CS.EXE. Remove this or use
another PC as the Communications Server.
Cannot Find the Key. If you are experiencing problems with the USB Features Key
here are some installation hints. First you must be at the computer you are installing
the Key on. The driver for the USB key cannot be loaded through a remote session
to that computer it must be done directly at the PC it is intended for. Next Load the
driver before plugging the Key in. Do not Plug the Key in before loading the driver.
If you did either of these remove the key and uninstall the driver and start over.
General, but essential guidelines are below.
1. If the Key is plugged in before the driver is loaded Windows will load the wrong
driver for it and it will not work even after the correct driver is loaded. If this
happens, the driver that Windows loaded must be removed. The Key must be
unplugged. The correct driver must be loaded and then the USB Key can be plugged
2. If the driver is loaded while the operator is logged into the server through a
remote session of any sort it will not work. You must have a keyboard and mouse
plugged directly into the PC that is to have the USB Key installed. Any type of
remote installation other than from the server itself will not work. The driver will
load and never find the key. If you then plug the key in, Windows will try to load
one and you are back where you started. Everything must be unplugged and
removed and you must start over from directly in front of the PC.
Note// Most people will skim through the instructions and see where we are going
and they will do this their way. There are 50 ways to do this and you would think as
long as we get to the same place it will be ok. There is only 1 way this will work and
it is this very specific way. From the PC itself load the driver and then connect the
History file getting too large?
In WinDSX 3.7.118 and higher, you can dictate how many days to keep in both
history logs in your system. When a file, created in notepad and saved as
DelHist.txt, is located in the WinDSX folder of the Comm Server or DailyOps PC, it
instructs the system to purge (mark for deletion) any system History and DataLog
information that is more than X amount of days old. Create the file on either
the Comm Server or DailyOps PC and name it DelHist.txt. Inside the file place a
number larger than 30. This is the number of days of history to keep. Once the
number of days have been exceeded the program will mark those events as deleted.
On even numbered calendar days, 2
, etc., the Log.mdb is pruned. On odd
numberd calendar days, the DataLog.mdb is pruned. To fully remove those events
you must close the program and run Repair and allow it to repair the History.
Note// The actual size of your log.mdb and datalog.mdb will NOT be reduced until
this last step is done.
Stackable Device Types
With Firmware Versions 3098 and higher (1040/22) and 569 and higher (1030/21)
Multiple device types can now be used simultaneously on the same reader.
In the past some Device Types such as D5 had multiple compatibilities. D5 would
decode standard 26 bit, DSX-33 bit, and DSX-37 bit.
With the newer firmware Multiple Device Types can be implemented (Stacked) by
assigning one Device Type that you need to Device 0 and the next one to
Device 1, the next one to Device 2, and so on.
1. If you are using the multiple compatibility of an existing Device Type and you
upgrade the firmware/flash in the controller(s), or once a new controller (containing
the new firmware/flash) has been added to the system, it will be necessary to assign
all of the Device Types required to the various Devices in the system.
2. If you require more Device Types than you have Devices, you can simply add an
additional Device and give it the Device Type you require even though
there will not actually be a controller with that address.
3. You cannot assign two different Device Types that are of the same bit length.
This means that you cannot have more than 1 device type of the same bit
length programmed in the system. There cannot be two different 26 bit formats or
two different 37 bit formats in the Device List. It is ok to have the same
Device Type more than once.
4. Once the different Device Types required have been addressed with the first few
devices in the list, the rest of the devices can have the same Device Type as
the rest of the list.
5. This feature only applies to Wiegand Formats. It cannot be used for Clock and
Data formats. Clock and Data formats are typically but not always used for
Magnetic Stripe and Barcode type readers.
6. The most common device types used for the Cards DSX sells is : WE-26bit, D5-
33bit, K0-35bit, L5-37bit.
Firmware 569 is now in production. A key change is the Stacked
Device Types. Instead of combination device types the panels try
to resolve the card read with any device type assigned to any
device in that location.
If the DSXFlash.exe program shuts down just after an attempted logon, the files
have probably not been copied to the WinDSX folder as directed in the How To
Flash*.txt file included with the transferred zip file.
If the DSXFlash.exe program fails to complete a firmware upgrade, shut down any
and all Anti-Virus and Firewall programs. These have been known to block
127.0.0.1 is a default TCP/IP address that can be programmed into WinDSX if not
connected to a network, or if on a network but no other PC’s are to run the
workstation portion of WinDSX.
For proper operation including printing of any sort from WinDSX, each
Workstation PC must have a unique Workstation Name and Workstation #.
Make sure a printer driver is loaded into the operating system. WinDSX software
needs a printer driver installed before reports can be run. A printer is only needed if
you want to print the reports to paper.
If the PC is not beeping on alarms, check the area Database>System
Parameters>Workstation Name>Yes/No Options and “Enable Beep on Alarm”.
Also, be sure Default Beep has been selected within the Operating System>Control
The WinDSX Comm Server program, cs.exe, can be run as a service in Version
3.7.34 and 4.8.6 and higher. The procedure and files necessary to do so are on the
Software Installation CD in the Docs and Utilities folders. In older versions cs.exe
can be placed into a startup folder.
Masking or not displaying the last User Name on the Login screen as per the
software installation manual only applies to the database program. To prevent the
Workstation program from displaying the last user name, it must be auto-started
from DataBase. With the placement of the GOV.exe into the shared WinDSX folder
the software will lockout an operator that makes three invalid attempts. Newer
software requires the password to be at least 6 characters.
Multiple iterations of the same event showing in workstation has been determined to
be caused by more than one Comm Server (cs.exe) running in a system. Can be
corrected also with new software.
Regional Time Zone and Daylight Savings Time settings
WinDSX has the ability to
set each location’s Regional Time Zone and enable or disable daylight savings time
(under Location in the database). The same is true for each workstation (under
System/Setup/System Parameters). If used, these options must be set for each
location and each workstation. Enable and set these everywhere. IF not
what you may see is that Workstation displays the correct time but events from the
controllers may show up with the wrong time.
Password Profile restrictions for I/O and Device Overrides not only apply to
operator manipulation of Inputs, Outputs, and Devices but to Scheduled Overrides
and Linking Level Assignments.
On an Elevator Control System with code to output linking turned on at a particular
device, the LED on the card reader does not change state on access granted unless
the option L
ink Granted Events to Output 1
is set to “Yes”.
Card Holders that are marked as a
cannot have an access level or linking
level assigned unless those levels have been defined (checked) as “Can be assigned
to Visitors” on the general tab.
Combinations of Code numbers that are HEX and DECIMAL values cannot be
entered into WinDSX in a combination of formats. Once we turn on “Codes are
HEX Values” then ALL code numbers MUST be entered into WinDSX as HEX
values. Use Windows>Calculator in scientific mode and convert decimals to HEX.
If codes are listed on cross reference sheets as decimal form and the “Codes are
HEX Values” is checked, then the decimal code number MUST be converted to
HEX and then entered into WinDSX using the HEX value.
The Time Zones that are being linked to cannot be assigned to what is initiating the
link. In other words – What links to the Time Zone cannot be controlled by the
Build as many Time Zones as necessary to make sure that when you link to a Time
Zone it only affects those things you want affected. Re-using Time Zones could
cause something to be controlled from a Link that was not desired.
If you link to a Time Zone with a Latch response you must have another Linking
Group that links to that same Time Zone with a response of Time Zone.
ASCII output from a Comm port on a Workstation is only used for Live Video
Camera Control such as pan, tilt, zoom. ASCII output for alarm or status change
on an input for camera call up will only work from the Communications Server.
The Log.mdb file, which contains all the transaction history, should be kept between
50 and 100 megabytes in size. When this file becomes too large it can cause History
reports to run slowly, or not run at all. In some cases, even the Delete Records
option(s) in the Backup History section may not work correctly. One solution is to
close the WinDSX program, copy the Log.mdb file to another folder, then delete the
original Log.mdb. The copied file will still be available for History reports prior to
this procedure. But if the size of the file is too large, reports may still be
questionable. When WinDSX is started again, a new Log.mdb will be created. It will
start recording history from Comm Server as of the date and time this procedure
Wildcard searches in UDF’s have changed. The wildcard characters are as follows:
where * and ? were heavily relied upon in the past, the % and _ are the replacement
characters. This change occurred in WinDSX software released around 09/25/2001.
As long as you have a 1040 or 1022 series controller as your Master, you can take
advantage of the DSXFlash program for firmware updates, even in a system mixed
with older controllers.
In Workstation in the Input screen if an input 7 goes into alarm there is a Red Box
flashing over the icon until the input returns to normal and the alarm is
acknowledged. If it goes into Door Held Open the red box flashes over the input 7
icon until the input returns to normal but does not have to be acknowledged.
When an input goes into trouble there is a yellow box that flashes over the input
icon while it is in trouble. When the trouble condition restores the yellow flashing
box changes to red. Trouble = yellow box, Trouble Restore = Red
The abort delay option will only delay the reporting of an Alarm condition for an
input. It will NOT delay the reporting of a Trouble condition for an input.
When "Use input 7 & 8", "Door Open detect relock", and "Exit request unlocks
Output 1" under Devices are all set to no, Input 7 can still trigger the PreWarn.
It doesn't really matter because once the input 7 has been disassociated with the
door the prewarn should not be used.
When you are using two devices to control the same door (in and out readers on the
same door) the PreWarn (sounder) of the Side B reader could be connected to the
prewarn output on side A.
PreWarn - During Locked period - Momentarily Unlock door (Card Read, REX
or Grant Access in Workstation) and prop door open. When Pre-Alarm starts
pulsing Unlock door via TZ (Regular schedule or Linking) or thru Workstation.
Pre-Alarm will continue to pulse
If the door is shut before the Held Open Time expires the Pre-Alarm will turn off.
If the door is shut after the Held Open Time expires the Pre-Alarm will continue to
The Pre-Alarm will keep pulsing until you Grant Access thru Workstation, activate
the REX input or use your card and get an Access Granted. Locking and Unlocking
the Output thru Workstation or via Time Zone will not stop the pulsing.
Cat5 cable cannot be used for anything in the WinDSX system
except for a network connection to a PC or LAN module.
The DSX-1030PR5 Intelligent Processor is used to upgrade existing DSX-1032,
1033, 1034 Intelligent Controllers. Mounts in metal enclosure that existing 1030P
comes out of with 4 existing screws. The DSX-1030PR5 has 512K of Flash ROM
and 512K of RAM.
The DSX-1020 is now a subset of the new DSX-1022. It has 2 Form C Relay
Outputs, 1 Reader Port, and 8 Supervised Inputs. It also has 512K of Flash ROM
and 512K of RAM.
The discontinued DSX-1021/1020 Intelligent Controllers do not perform the battery
test at 10:00AM like the discontinued 1030 Series Intelligent Controllers do. The
new DSX-1022 does perform the Battery Test. The DSX-1040 PDM has an input
to trigger the battery test. It is connected to an open collector output on a 1040
Series Controller and activated by a Time Zone assigned to the output.
The backup battery runtime for a 1048 may provide as little as 30 minutes. The
amount of time provided is dependent on panel load. Properly adding more batteries
can provide more time of battery power.
No Lock power from a DSX-1042 could be caused by the fire override having an
open condition on the Fire Override input of the 1040-PDM. Place a short across
the input and lock power should restore for locks 1-8. A closed circuit from the Fire
Alarm System can also be connected to the Fire Override input. This circuit should
go “open” on a fire alarm condition.
There is no +5 VDC on a DSX-1042 Intelligent Controller. Use
caution when wiring readers to the 1042 panel. Readers will not
work if they are wired improperly. However, there is 5VDC @
.375amps available on the 1040-CDM for 5 volt devices.
On the 1040-CDM, jumpers 1 & 2 should be set properly to
indicate if there is a Master Controller, (dip switch 8 on)
within that enclosure. Jumpers connected to the 2 left pins =
all controllers in this enclosure are Slaves. Jumpers connected
to the right 2 pins = a Master controller exists within this
If there appears to be no control of relays on a DSX-1043 Intelligent Controller,
make sure it is defined with a Device Type of “OR”. Also, make sure there is a short
between the Relay Override input terminals near the center of the Controller.
These were pins 24-25 on older 1043’s, pins 50-51 on newer 1043’s.
The 150/15 power supply, intended to provide power for all 1040 Series Intelligent
be used to provide lock power as well. A separate power
be used for lock power.
When troubleshooting a reader on a 1042 panel, take the reader to the DSX panel
and terminate it directly to the reader port. If the reader works fine at the panel,
check the field wire for ground faults and shorts. If there are no faults or shorts on
the wire, contact DSX Technical Support. A new processor may be required to fix
All unused inputs on all DSX Intelligent Controllers
be terminated with 1K
resistors except for the DSX-1033 and 1043 Output Controllers.
Communications loss when relay outputs are cycled (energized or de-energized) is
commonly due to a counter EMF spike. Counter EMF spike is best described as the
collapsing of the magnetic field when a coil is de-energized. When a door strike or
maglock is powered down. The magnetic field collapses and the energy must go
somewhere. It is important to switch positive power to the coil driven device and
keep the ground to that device constant and place an MOV across the connections
from your wire to the device. This allows the MOV to activate when the field spikes
to high and shunt the energy to the ground wire right at the device. Troubleshooting
this is simple. Cycle one or more relays up to 50 times or until the comm. loss
occurs. Then remove the wiring from the relays you are testing and cycle them again
and this time there should be no comm. losses. Try the same test
again once you have wired the device with a constant ground and an MOV. Use
different MOVs for 12 and 24V locks.
Modem power polarity is important. Proper polarity is to wire the center pin of the
modem’s power connector to positive and the outer shell or outside of the
connector to negative. Always power the modem from the panel.
For older (non-metal) modems, if the modem answers but does not transmit
information, make sure the DSX panel has tried to dial out. Power up the DSX
panel and the modem at the same time. The DSX panel should try to dial within two
minutes. Once the panel has dialed out once, unplug the data wire going into the
DSX panel. Dial the DSX panel from the Communications Server PC. When the
modem answers, plug the data wire back in. The system should start communicating
Newer DSX modems are configured at the factory with the correct init string.
WinDSX is not compatible with Windows 95, Windows 98 or Windows ME or any
Home Version of OS. WinDSX always requires the professional or business version
of Operating System.
With WinDSX 3.5 or higher, in Workstation you can toggle between the displaying
of inputs, outputs, and device names and their actual addresses. For example,
“Front Door Lock” in location 4 could appear as 4.0.1. This is a great help when
calling for Tech Support. We know our address numbers; we don’t know your names. Click
on an individual input or output in Workstation and type xsd (DSX backwards).